I wonder, which code or table is require to determine a distans from Storage of Liquids (Fuel) in Underground Tanks to school or any public buildings?
See NFPA 30 chapter 23 for general distances from underground storage tanks to important buildings and/or property lines. Local ordinances will also apply.
NFPA 30 chapter 23 doesn't determine a distances to other property line, this issue determines chapter 24 but that distance is very very little for fire safety. and i'm interested in if any other nfpa code determines regulation for this issue
See NFPA 30 (2018) in Chapter 23 para 23.4.2 and 23.4.3 below:
23.4.2 The distance from any part of a tank storing Class I liquid to the nearest wall of any basement or pit shall be not less than 1 ft (0.3 m) and to any property line that is or can be built upon shall not be less than 3 ft (0.9 m).23.4.3 The distance from any part of a tank storing Class II or Class III liquids to the nearest wall of any basement, pit, or property line that is or can be built upon shall be not less than 1 ft (0.3 m).
The keyword there for you is "property line" which is the boundary between your facility and others e.g. the public.
Retrieving data ...