NFPA 101:220.127.116.11 discusses alarms OR detectors and directs us to 18.104.22.168.2 for system. Is it the intent that a smoke alarm directly outside a bedroom is allowed with single- / multi-station household alarms and system detectors shall be installed to manufacture specified spacing as we would install in a commercial system per NFPA72 chapter 17.
Where a household alarm system exists with 85 db sounders built-in to the system smoke detectors, bedrooms have sounders built on smoke detectors. Interconnection is not required on existing single- / multi-station. In the smoke detection system per 22.214.171.124 is the intent of code to require full occupant notification or only the detector audibility?