Does Article 230-3 apply to Modular Duplex dwelling, ie, can an S E Cable pass through unit 1 to reach unit 2?
I'm working on an incident in an aerosol manufacturing facility. The following question has nothing to do with the incident. However while doing a quick walk through from the incident area, I noticed a bonding/grounding technique, that I believe isn't correct. The company uses the clamps from battery jumper cables as the attachment